000047 L - compteur eau pré-filtre mis en place

INTERVENTION POUR MISE A JOUR DE LA MACHINE
MISE A JOUR FW2.12 + FW2.2
V3 0111
CELLULE N°C600067

PB DE SEL TROP HAUT DANS RESERVOIR SAUMURE ET TROP BAS DANS ADOUCISSEUR

MIS EN PLACE DE CLIPS SUR LES POMPES
MISE EN PLACE D'UN COMPTEUR
REMISE EN MAIN D'UN CLASSEUR + BANDELETTES
FORMATION 1ER NIVEAU A L'OPERATEUR

CAPTEURS DE SEL INVERSES!!! RAS REMIS DANS LE BON SENS!!
MISE A JOUR DE LA LIGNE HYDRAULIQUE SAUF DEBITMETRE

TENSION DEPART 6.8V